EDC2012NC - Tower Standpipe with 1/2" Non Concussive Tap
Frequently Bought Together:
- Non-Concussive chrome tap - Self Closing Bib Tap With Front Press
- High quality stainless steel construction.
- Solid DZR brass internal plumbing.
- Lockable and secure.
- WRAS approved OEM backflow prevention device.
- Suitable for fluid category 3 risk.
- Simple MDPE push fit connection.
Manufactured in high quality stainless steel, the EDC2012NC is the definite choice for a safe and secure water supply.
This is a non-concussive product in complete chrome finish. This faucet features automatic close and front press lever.
The EDC2012NC standpipe is ideal for all areas of public access. This includes retail parks, private and public spaces, residential, recreational spaces, marinas, caravan sites, vehicle washing stations and allotments.
The EDC2012NC is fitted with Edwards Engineering’s own WRAS approved OEM backflow prevention device (WRAS 1912015), which includes a double check valve. This is suitable for applications that require protection against a Fluid Category 3 risk.
The high quality stainless steel shell offers: longevity, durability, pleasing aesthetics and features a lockable cover for vandal resistance.
Internal parts are all made of high quality DZR Brass and conform to industry water standards.
Installation and Maintenance
The EDC2012NC is designed to be connected below ground. The unit should be buried in the ground to a level of 750mm, allowing for an above ground profile of 730mm. Simply backfill the installation hole to secure the unit.
The EDC2012NC also incorporates a servicing valve, which can be accessed by either removing the front or back maintenance panels with the supplied Allen key.
Although this unit has been designed to accommodate fluctuations in severe weather conditions, it is important that in extreme cold weather, it is recommended that the service valve is shut off and the outlet tap is left open.
Please call 01584 861223 or firstname.lastname@example.org for further information.
N.B. The water user must decide upon the backflow requirements necessary for each installation.
EDC2012NC Standpipe Specification:
|Material||Brushed Stainless Steel (Grade 304 - 1.5mm Thickness)|
|Unit Length||1480mm (730mm above ground profile - 750mm installed below ground)|
|Unit Section||110mm x 130mm|
|Outlet Tap Cover||250mm x 180mm x 130mm|
|Stabilising Base Plate||250mm x 230mm|
|Blackflow Prevention||3/4” OEM Double Check Valve & Isolation Valve - DZR Brass Body. (Edwards Engineering Ltd - WRAS 1912015)|
|Outlet Tap||1/2” Non-Concussive Tap (Chrome Finish)|
|Inlet Connection Type||25mm B Push DZR Brass Coupler|
|Mains Connection||25mm MDPE (Not Supplied)|
|Pressure Supply||10 bar maximum|
|Insulation||Polyflex expanded foam or equivalent insulator, giving protection down to -5 degrees Celsius|